Swimming Pool / Spa
Linn County Public Health
1020 - 6th Street SE
Cedar Rapids, IA 52401
Phone: (319) 892-6000 Fax: (319) 892-6099
Facility Name: Red Roof Inn Cedar Rapids
Registration No: SP57-016-100
Notes: Pool is to remain closed until cyanuric acid levels are measured at or below 40ppm.
|Comment: Not able to verify documentation for main drain covers VGB compliance and dates of installation.|
|Item: Main drain and Safety Vacuum Release System documentation (VGB) with dates of installation must be kept in facility. Each SVRS shall be tested monthly and the test dates recorded|
|Comment: Not able to verify records of monthly ground fault circuit interrupter testing in operational records.|
|Item: Monthly ground fault circuit interrupter (GFCI) shall be included in Operational Records|
|Comment: Pool cyanuric acid concentration was in excess of 100ppm. Pool to remain closed until CYA levels are measured at or below 40ppm.|
|Item: Pool / Spa shall be closed if cyanuric acid concentration in spa exceeds 80 ppm|
|Report Received By:||Received:|
These items must be corrected as soon as possible in order to comply with the Iowa Department of Public Health Swimming Pool and Spa Rules. A letter regarding the actions which will be taken in order to correct all deficiencies must be submitted within 30 days to this office. If for any reason you take issue with any of the items cited regarding swimming pool rules, a variance can be requested by following the instructions in the Iowa Department of Public Health Swimming Pools manual, amended July 8th, 2009, page 57, section 641-15.7 (135I). Variance requests regarding spa rules must be made in compliance with the instructions in the Iowa Department of Public Health Spa manual, revised July 8th, 2009, page 32, section 641-15.7 (135I).